1.1 kV (A.C) & 1.5 kV (D.C ) to Earth
1.5 Sq. mm copper conductor, PVC insulated unarmoured & galvanised steel strip / wire armoured control cables as
per IS 1554 Part – 1.
Conductor : CU conductor solid as per Cl.1 IS 8130 or stranded as per Cl. 2 IS 8130
Insulation Material : PVC Type – A as per IS 5831 / Option : HR PVC (Type – C ) as per IS 5831. Nominal Thickness of
Insulation is 0.8 mm.
Core Colours : Up to 5 cores by colour coding & more than 5 cores number printing on core as per IS 1554 (P-1)
Inner Sheath : PVC / PVC tape as per IS 1554 (P – 1)
Armouring : Single armouring of galvanised steel strip / wire
Outer Sheath : PVC Type ST – 1 as per IS 5831 (Option : PVC Type ST – 2 as per IS 5831, FR Type / FRLS Type)
Cable Color : Black (Options : Any other color as per requirement)
Cable Design Parameters
While ordering, in addition to the part number the following details shall also be advised:
Conductor Type (Aluminium or Copper) and class of conductor (Cl. 1 or 2).
Insulation Type – PVC Type A / C.
Sheath Type – PVC Type ST-1 / FR / FRLS; PVC Type ST-2 / FR / FRLS.