1.1 kV (A.C) & 1.5 kV (D.C ) to Earth
1 cores AL / CU conductor, PVC insulated, aluminum steel strip / wire armoured cables as per IS 1554 Part – 1.
Conductor : AL up to 10 Sq. mm conductor are solid Cl. 1 as per IS 8130. And above 10 Sq. mm conductor
are stranded round or compact Cl. 2 as per IS 8130
In CU 4 & 6 Sq. mm conductor are solid Cl. 1 or stranded Cl. 2 as per IS 8130. 10 Sq. mm & above stranded
round or stranded compact Cl. 2 as per IS 8130
Insulation : PVC Type – A, as per IS 5831.( Option : HR PVC Type – C, as per IS 5831)
Core Color : Red or yellow or blue or black or natural
Armouring : Single armouring of aluminum wire or aluminum strip as per IS 1554 P – 1
Outer Sheath: PVC Type ST – 1 as per IS 5831 (Option : PVC Type ST – 2 as per IS 5831 / FR Type / FRLS
Cable Color : Black (Options : Any other color as per requirement)
Cable Design Parameters
While ordering, in addition to the part number the following details shall also be advised:
Conductor Type (Aluminium or Copper) and class of conductor (Cl. 1 or 2).
Insulation Type – PVC Type A / C.
Sheath Type – PVC Type ST – 1 / FR / FRLS; PVC Type ST – 2 / FR /FRLS.
Colour from above technical detail.