1.1 kV (A.C) & 1.5 kV (D.C ) to Earth
4 Cores AL / CU conductor, PVC insulated, galvanised steel strip / wire armoured cables as per IS 1554 Part – 1.
Conductor : AL up to 10 Sq. mm conductor are solid Cl. 1 as per IS 8130. And above 10 Sq. mm conductor are
stranded compacted shape Cl. 2 as per IS 8130
In CU 4 & 6 Sq. mm conductor are solid Cl. 1 or stranded Cl. 2 as per IS 8130. 10 Sq. mm conductor is stranded Cl. 2
round as per IS 8130. Above 10 Sq. mm conductor are stranded compacted shaped Cl.2 as per IS 8130
Insulation : PVC Type – A as per IS 5831. (Option : PVC Type – C as per IS 5831)
Core Color : Red, yellow, blue, black
Inner Sheath : PVC / PVC tape as per IS 1554 (P-1)
Armouring : Single armouring of galvanised steel strip / wire
Outer Sheath : PVC Type ST – 1 as per IS 5831 (Option : PVC Type ST – 2 as per IS 5831, FR Type, FRLS Type)
Cable Color : Black (Options : Any other color as per requirement)
Cable Design Parameters
While ordering, in addition to the part number the following details shall also be advised:
Conductor Type (Aluminium or Copper) and class of conductor (Cl. 1 or 2).
Insulation Type – PVC Type A / C.
Sheath Type – PVC Type ST-1 / FR / FRLS; PVC Type ST-2 / FR / FRLS.