1.1 kV (A.C) & 1.5 kV (D.C ) to Earth
2 cores AL / CU conductor, PVC insulated, galvanised steel strip / wire armoured cables as per IS 1554 Part – 1.
Conductor : AL up to 10 Sq. mm conductor are solid Cl. 1 as per IS 8130. And above 10 Sq. mm conductor are stranded round or compact round or compact shape conductor Cl. 2 as per IS 8130
In CU 4 & 6 Sq. mm conductor are solid Cl. 1 or stranded round Cl. 2 as per IS 8130. 10 Sq. mm conductor is stranded round or stranded compact conductor Cl. 2 as per IS 8130
Above 10 Sq. mm conductor are stranded round or compact round or compacted shaped Cl. 2 as per IS 8130.
Insulation : PVC Type – A, as per IS 5831. (Option : HR PVC Type – C, as per IS 5831)
Core Color : Red, black
Inner Sheath : PVC / PVC tape as per IS 1554 (P – 1)
Armouring : Single armouring of G.I. Wire or G.I. Strip as per IS 3975
Outer Sheath : PVC Type ST – 1 as per IS 5831 (Option : PVC Type ST – 2 as per IS 5831 / FR Type / FRLS Type)
Cable Color : Black (Options : Any other color as per requirement)
Cable Design Parameters
While ordering, in addition to the part number the following details shall also be advised:
Conductor Type (Aluminium or Copper) and class of conductor (Cl. 1 or 2).
Insulation Type – PVC Type A / C.
Sheath Type – PVC Type ST – 1 / FR / FRLS; PVC Type ST – 2 / FR /FRLS.